We have seen that neither of the two methods, M.M.F. method and E.M.F. method is capable of giving the reliable values of the voltage regulation. The error in the results of these methods is mainly due to the two reasons,

1. In these methods, the magnetic circuit is assumed to be unsaturated. This assumption is unrealistic as in practice. It is not possible to have completely unsaturated magnetic circuit.

2. In salient pole alternators, it is not correct to combine field ampere turns and armature ampere turns. This is because the field winding is always concentrated on a pole core while the armature winding is always distributed. Similarly the field and armature m.m.f.s act on magnetic circuits having different reluctances in case of salient pole machine hence phasor combination of field and armature m.m.f. is not fully justified.

Inspite of these short comings, due to the simplicity of constructions the ASA modified from of M.M.F. method is very commonly used fore the calculation of voltage regulation.

Fig. 1 |

Consider the phasor diagram according to the M.M.F. method as shown in the Fig. 1 for cosΦ lagging p.f. load. The F

_{R}is resultant excitation of F_{O }and F_{AR }where F_{O }is excitation required to produce rated terminal voltage on open circuit while is m.m.f. required for balancing armature reaction effect. Thus OB = F

_{R}= resultant m.m.f. The angle between F

_{AR }and perpendicular to F_{O }is Φ, where cosΦ is power factor of the load. But OB = F resultant is based on the assumption of unsaturated magnetic circuit which is not true in practice. Actually m.m.f. equal to BB' is additional required to take into account the effect of partially saturated magnetic field. Thus the total excitation required is OB' rather than OB.

Let us see method of determining the additional excitation needed to take into account effect of partially saturated magnetic circuit.

Construct the no load saturation characteristics i.e. O.C.C. and zero power factor characteristics. Draw the potier triangle as discussed earlier and determine the leakage reactance X

_{L }for the alternator. The excitation necessary to balance armature reaction can also be obtained from the potier triangle. The armature resistance is known. Construct ASA diagram, and draw phasor diagram related to the above equation.

The ASA diagram has x-axis as field current and y-axis as the open circuit voltage. Draw O.C.C. on the ASA diagram. Then assuming x-axis as current phasor, draw V

_{ph }at angle Φ, above the horizontal. The V_{ph }is the rated terminal voltage. Add I_{a }R_{a }in phase with I_{a }i.e. horizontal and I_{a }X_{L }perpendicular to I_{a }R_{a }to V_{ph}. This gives the voltage E_{1ph}. Now with O as a central and radius E

_{1ph}draw an arc which will intersect y-axis at E_{1}. From E_{1}, draw horizontal line intersecting both air gap line and O.C.C. These points of intersection are say B and B'. The distance between the points BB' corresponding to the field current scale gives the additional excitation required to take into account effect of partially saturated field. Adding this to F_{R }we get the total excitation as F_{R}**'**. From this F_{R}**'**, the open circuit voltage E_{1ph}can be determined from O.C.C. using which the regulation can be determined. The ASA diagram is shown in the Fig. 2.Fig. 2 |

The resultant obtained by ASA method are reliable for both salient as well as nonsalient pole machines.

**Sponsored links :**
## 0 comments:

## Post a Comment